Ground-breaking housing scheme captures one developer’s journey to passive
The just-finished second phase of Durkan Residential’s ambitious Silken Park scheme in south-west Dublin bridges the gap between two extremes: while phase one was built to the 2002 building regulations, phase three — which will break ground next year — will comprise 59 passive certified units.
This article was originally published in issue 18 of Passive House Plus magazine. Want immediate access to all back issues and exclusive extra content? Click here to subscribe for as little as €10, or click here to receive the next issue free of charge
When phase one of the Silken Park development in City West, Dublin was completed in 2007, the 22 apartments and 33 houses were built to 2002 regulations, and featured partial fill cavity walls and permanent wall vents, with no provision for airtightness.
Phase two, which was completed recently, includes 15 houses. Each boasts highly insulated, single leaf walls, airtightness that in many cases beat passive house levels, and demand controlled ventilation.
And phase three – on which work has begun – will showcase 59 certified passive houses.
Once complete, it will be, by some distance, the largest passive house development in Ireland. Though the company behind Silken Park is a well-known large scale developer, Durkan Residential is family run — by brothers Patrick and Barry Durkan. Through the early part of the last decade, they specialised in housing for first time buyers, and completed major residential developments in Finglas and Greystones. Silken Park was very much in that mould. Back then, the company sought and received permission for 149 units, completing the first 55 in 2007.
The ground floor features 150mm of Xtratherm insulation under the concrete slab and 100mm Xtratherm as an upstand to the inside of the blockwork around the entire perimeter to reduce thermal bridging.
“We were focused hugely on finish,” says Patrick Durkan. “We did superior kitchens, quartz worktops, Rationel windows...Although an entry level home, we put a lot of emphasis on interior design and getting a really high quality finish.” Then the crash hit and everything stopped. Phases two and three of Silken Park went into mothballs, the planning permission expired and nothing happened for nearly seven years.
By the time the Durkans were able to realistically consider starting again, everything had changed. The building regs were significantly tighter, as were lending conditions, while the market itself was unrecognisable from the heady days of the mid-noughties. The one thing that remained the same was the company’s commitment to delivering a quality product. But while that commitment used to manifest itself in finishes and interior design, it now found a new means of expression.
(Clockwise from left) Rockwool’s REDArt Silicone external insulation system being fitted to the concrete block walls; installation of the windows flush with the external insulation layer; the exterior walls are clad with the BrickShield system to create a real brick finish.
During the downturn, the Durkans had closely followed developments in the only corner of the building industry that showed any signs of life – the refurb market. They had seen how emerging insulation techniques and products could transform substandard housing stock.
Other factors were also at play. “There were a variety of influences,” says Patrick. “What was going on in Europe, the refurbishment market, the implementation of BCAR, Part L. We became focused on achieving a more cost-effective house without compromising the product.”
Looking around at how other developers were reacting to these influences, he saw both bad and good. “A lot of developers throwing PV on roofs, or sticking in heat pumps...piling on renewables. We said, why not focus on building a better house, so you don’t need to place too much emphasis on renewable technologies to reach targets.”
To realise this ambition, the Durkans brought architect and sustainable design consultant Jay Stuart – technical director of Durkan’s building fabric contracting company, Ecofix – on board and charged him with coming up with a specification that would deliver low energy at low cost.
(Clockwise from top left) Pro Clima Intello membrane fitted to the underside of ceiling rafter; careful taping at window reveals; webjoists are wrapped in membrane for an airtight loop, membrane taped back to the wall with Solido plasterable tape and for extra safety, the plasterer plastered over as much surface as possible – even between webjoists and over the membrane.
“The objective for the phase two houses,” says Stuart, “was to build better houses by focusing on integrating a designed ventilation system, a high degree of airtightness, minimal thermal bridging and high thermal performance.”
He knew that if the build team could achieve this, they would deliver healthy houses with almost no risk of condensation, high indoor air quality, a high degree of thermal comfort and low heating costs. “The challenge was achieving a high degree of airtightness and minimal thermal bridging cost effectively, with some standard and some innovative but simple details.”
To that end, Stuart set about creating a series of construction details that could be applied uniformly across all units in phase two. Each one was subject to analysis by industry-leading professionals, to ensure they delivered across a range of criteria, including U-values, thermal bridging and Deap assessment.
Take just one of the details that Stuart zeroed in on: the gang nail roof truss. Ubiquitous in roof construction in Ireland, it has, says Stuart, represented something of a weak point in the insulated envelope. “When you’re talking about current regs, you need quite a thickness of insulation, but that insulation gets pinched by the geometry of the house at the junction of the wall plate. And what happens inside the house? Hot air rises, it carries humidity with it and it condenses wherever there’s a thermal bridge or a reduction in insulation, and that’s really in the corner of all bedrooms in all houses. If you solve that junction, you improve all sorts of things, including reducing the risk of condensation.”
Taking up that challenge, Stuart sat down and designed a new detail that would overcome this weakness. He had it tested to ensure it delivered optimal performance, and then took it to Durkan to find out what kind of premium would be required to deliver that specification. The answer was zero. “A little bit of thinking costs nothing,” says Stuart, “Good detailing is not expensive.”
Ventilation is provided by an Aereco demand controlled mechanical extract ventilation system, with humidity sensitive air inlets.
He goes on to say that the view expressed by some sections of the industry, that more demanding building standards somehow inhibit construction activity by driving up costs, has no basis in fact. Patrick Durkan agrees. He says that the decision to go for such a high spec product in phase two, and a fully passive one in phase three, was market-led.
“The challenge was to work with our financial partners to build something that was really cost-effective but make it as efficient and attractive and saleable as possible...We don’t talk about eco or green or passive. Believe it or not, that’s just a by-product of what we’re marketing.”
And nor will you see the words ‘green’ or even ‘passive’ in Durkans’ Silken Park brochure. As far as the market is concerned, price trumps all other variables. Central bank lending restrictions have been instrumental in choking off funding for first time buyers, making price the most important variable for those looking to get a foot on the property ladder.
“The market is about value for money, the market is about affordability,” says Durkan. “In terms of people getting mortgages, we need to be very conscious of the price point...We have to deliver these houses at a price that satisfies our investors. That’s the challenge.”
In addition to drawing up those critical construction details, Jay Stuart also drew on his extensive work in the retrofit market with Ecofix to specify external wall insulation on all units. “The major change and biggest saving was to build the external walls as single leaf hollow block, externally insulated with Rockwool EWI systems,” says Stuart, who commissioned Wufi calculations to be certain that Rockwool – in this case variously finished with Rockwool’s REDArt Silicone and BrickShield external insulation systems, which features a real brick finish – would work with single leaf block walls in this climate.
A blower door test was carried out by Building Envelope Technologies to measure the air leakages in the building; with smoke pencils used to identify localised leakage.
The calculations showed that the moisture content of the whole construction decreased over time and that the thermal performance was good and in line with standard U-value calculations. To repeat, these are hollow-block walls – the much-denigrated staple of Irish house-building that has persisted for so long in the Dublin region in particular. Jay Stuart points out however that EWI makes the build method less important than you would think.
“If you’re using external insulation, you could build the single leaf masonry wall from anything. Once it’s structurally stable, and the engineer’s happy with it, I don’t care what it is.” Stuart’s point is well made. The thermal performance and interstitial condensation issues associated with hollow block construction were really about the combination of leaky plasterboard and internal wall insulation that typically went with it. As Joseph Little’s seminal Breaking the Mould series of articles in this magazine’s predecessor, Construct Ireland, showed, dry lined hollow block walls may present a significant risk of interstitial mould. The failing lies with the build-up, not with hollow blocks per se.
The method chosen at Silken Park also had the major cost advantage of going up very quickly – reducing build times to 14-16 weeks compared to 18 weeks for a cavity wall house.
On phase one, the build team took no real airtightness measures, as the notion of sealing buildings up was in its infancy in Ireland at the time. On phase two however, the airtightness strategy was exemplary, and delivered results as low as 0.29 ACH – among the best results ever achieved in this country – ably assisted by experienced airtightness contractor Roman Szypura of Clioma House.
With great airtightness comes great ventilation – or at least it should. In phase two of Silken Park, the decision was taken to go with an Aereco demand controlled mechanical extract ventilation system. There are two major advantages to this system — it’s maintenance free and has exceptionally low running costs.
It does tend to be less efficient than heat recovery ventilation, says Jay Stuart, but tests have suggested that the shortfall is only in the order of 8 to 12 per cent.
In order to meet the renewable energy obligations under Part L of the building regulations, a kilowatt worth of solar PV panels from Warik Energy was placed on the roofs of the phase two homes. And as this phase approaches completion, the design and build teams will soon turn their attention to the 59 fully certified passive houses that will comprise phase three.
“We’ve wanted to get to passive house, to a new standard of construction,” says Patrick Durkan. “But we didn’t want to jump straight there, that would have been too great a departure for us.”
The reality however is because of the build quality in phase two, going that final step to passive is no more than that, a step. A report by James Walsh of Low Energy Design revealed that only a few changes have to be made to the specification. The demand controlled ventilation system will be replaced by MVHR, the windows will be upgraded to triple-glazed while the building envelope will need a slight increase in insulation levels – with 40mm more Rockwool for the external insulation system.
In addition, the design team has decided to streamline systems within the new units by going for all electric appliances and equipment. Patrick Durkan is looking to the day when phase three homeowners can put PV on the roofs of their houses to take care of their energy needs, and perhaps even sell energy back to the grid.
With this in mind, Jay Stuart says that there may be an opportunity to build a zero energy house in this phase.
“If so,” he says, “it will be among the first commercially built NZEB houses in Ireland. We know how to do it and we know the costs but we’ll all have to wait to see what happens. There is more to be learned and we will share our journey in the next chapter of our story.
Selected project details
Developer: Durkan Residential
Architect: BBA Architecture
Main contractor: Durkan Residential
M&E Engineer: Murphy Belton Consulting Engineers
Civil & structural services: O’Connor Sutton Cronin & Associates
Energy consultant: Low Energy Design
Mechanical contractor: Mowlds Heating and Plumbing
Electrical contractor: JP Byrne & Company
Airtightness contractor: Clioma House
Airtightness testing: Building Envelope Technologies
External wall insulation: Rockwool
Building envelope & airtightness contractor: Ecofix
Roof & floor insulation: Heiton Buckleys
Airtightness products: Ecological Building Systems
Windows & doors: Rationel Vindeur
Demand controlled ventilation: Aereco
Solar PV: Warik Energy
Fit out: Cawleys Furniture
Roofing supplier: Roadstone
Roofing contractor: Neal Brennan
Landscaping: Redlough Landscaping
Sand/cement render (airtight layer): Kilsaran
Building type: Phase two of private development, consisting of a mix of terrace and semi-detached. Eight two-storey terraced houses (74.5m2), six three-bed semi-detached houses (90.8m2), and one four-bed detached house (125.8m2).
Location: Citywest, Co. Dublin.
Completion date: March 2016
Passive house certification: N/A
PHPP/DEAP figures below are for three-bedroom, semi-detached units
Space heating demand (PHPP): 51kWh/m2/yr
Heat load (PHPP): 18 W/m2
Primary energy demand (PHPP): 118 kWh/m2/yr
Energy performance coefficient (EPC): 0.393
Carbon performance coefficient (CPC): 0.344
Environmental assessment method: N/A
Airtightness: 9 of the 15 houses in phase 2 achieved less than 0.534 ACH at 50 Pa, well below the passive house target. The worst airtightness test result on completion was 0.812 ACH at 50 Pa.
Thermal bridging: Floor slab built using a traditional strip foundation, plinth insulated with dense/waterproof EPS right down to the foundation. Fixed 100mm Xtratherm as an upstand to the inside of the block around the entire perimeter. Joist junction using Durkan details: 0.077 W/mK. The brief was to draw a continuous line around the building and ensure the thermal line remained intact. Using Durkan’s own details all doors and windows are set in the insulation zone. Roof junction detail worked very well ensuring adequate ventilation. Not breaking thermal line has proven difficult here because of the tight angle, however by changing truss details slightly a psi-value of 0.077 W/mK was achieved.
Ground floor: Strip foundation using concrete blocks,150mm Xtratherm insulation, concrete slab. U-value: 0.15 W/m2K
Walls: Single leaf 215mm concrete block wall finished externally with Rockwool’s REDArt Silicone and BrickShield external insulation systems, including 160mm Rockwool semi-rigid insulation and 15mm sand/cement render internally as the airtight layer. 16mm electrical services zone and 12.5mm plasterboard on dabs finished with wet skim coat plaster. U-value: 0.20 W/m2K
Roof: Roadstone black concrete roof tiles, on 50X35mm battens, followed underneath by breathable Pro Clima Solitex underlay, attic trusses as designed by Shannonside Engineering fully fitted with 100 Knauf Ecose insulation, fitted between joists with another 150mm criss crossed over, with a final layer of 100mm crossed over. Pro Clima Intello membrane tacked to underside of ceiling rafter and taped at overlaps and wall junctions. 25mm battens countersunk into rafter for service void. 12.5mm plasterboard ceiling and skimmed internally. U-value: 0.1 W/m2K
Windows: Rationel Aura Range double glazed timber windows. FSC-certified laminated Scandinavian pine. Fully certified by the Wood Window Alliance. Overall U-value: 1.34-1.62 W/m2K
Heating system: Vokera Mynute I20 modulating 92% efficient condensing gas boiler supplying heating to conventional wall radiators and 300 litre buffer tank.
Ventilation: Aereco demand controlled mechanical extract ventilation system.
Electricity: Four 250W solar PV panels per dwelling.
Green materials: All timber furniture from FSC/PEFC certified sources.
- Analysis: 12,000+ homes built in 2017 – as energy standards marginally fall
- South London scheme delivers better health for residents
- New homes data reveals extent of Irish low energy revolution
- Active learning at Aberdeen passive nursery
- Ireland’s largest passive house scheme shows way to nZEB
- Kiss House launches “cutting edge” turnkey passive houses
- How to prevent condensation & mould
- SuperHomes scheme: a blueprint for cost-effective deep retrofit?
- Solihull upgrade trials revolutionary retrofit approach
- Deep retrofit transforms big, complex South Dublin home
- Yorkshire passive house pushes cavity wall boundaries
- UK's largest passive building opens to 2,400 students and staff
Latest from John Hearne
- The PH+ guide to External Insulation
- North Dublin sheltered scheme makes A1 breakthrough
- Dublin boiler house reborn as green building exemplar
- A green builder's dream green home
- Out of control? Are building control systems properly equipped to deliver safe, healthy and well-constructed buildings?
- A2 rated Rathgar scheme goes high end but low energy